Water Hardness Scale Chart – What Size of Water Softener Do You Need? Articles Water Softener Guides Water Softener Information By Ryan Walker / April 7, 2016 Share Tweet Pin Share Share Water Hardness Scale Chart – What Size of Water Softener Do You Need?3.3 (65%) 4 votes The whole way across the web one can find websites and reviews that help people to pick the best water softener. Tragically by far most of these apparatuses neglect to join water softener effectiveness into the figuring. The outcome is frequently a decision of softener that appears to be appropriately estimated yet brings about huge salt utilization (regularly more than 2000 pounds for every year) rather than an effectively measured, proficient model that uses 300 pounds over that year. Why does this happen? It is basically that numerous merchants – both online and in-store – don’t comprehend the idea of softener salt proficiency and don’t join it into their measuring model. Why Should I Care About Efficiency? The productivity of your water softener directs the amount of salt you need to purchase, the amount of salt you need to drag, and the amount of salt gets released to nature. Measuring a softener and considering its salt effectiveness will guarantee you buy a softener that never comes up short on delicate water additionally utilizes a minimal measure of salt as could reasonably be expected. Over the life range of the water softener, this means huge cost reserve funds and simplicity of proprietorship. Also Read: Water Softener Prices – An Overview Water Hardness Scale Chart This is the measure of the amount of calcium and magnesium dissolved in your water. Contingent upon where a water test is performed this data will be accounted for in mg/L (milligrams per Liter) or GPG (grains per gallon). Grains per gallon is the business standard approach for talking about water hardness. Jumping mg/L by 17.1 will change it to GPG. A “grain” of water hardness is comparable to 1/7000th of a pound. Formula to measure no of grains to be removed: If hardness is in MG/L or PPM , convert it into GPG by dividing it with 17.1. No of Persons * 75 Gallons * ( No of GPG + mg/lit Iron) = Total grains to be removed per day. Note: If you’re living in a city, enter the mg/lit Iron as ‘0’. What Size of Water Softener Do You Need? For private,non-commercial and residential drinking water application we ordinarily prescribe that a water softener is recovered about once every week. Amid recoveries, high groupings of sodium chloride sterilize and clean the sap bed. On the off chance that you have iron in the water, a gum cleaner added to the sodium chloride will help in diminishing fouling and will help the gum last any longer. With most water softeners you will have a decision of salt settings. We, as a rule, prescribe that private softeners be recovered at a 8 lb. per ft3 low salt setting. The accompanying data depends on these parameters. In the event that we take the Daily Softening Requirement of 3000 grains for each day and various this by 7 days, we require a softener that can diminish 21,000 grains of aggregate hardness to recover once every week. For small and medium households with up to 6 family members and 2-3 bathrooms, Fleck 5600SXT is the best system. For large households and offices, we recommend the Fleck 7000SXT model which has a capacity of 64,000 grains. A snappy look of online and in numerous stores will uncover a plenitude of 24,000/32,000/48,000/and 64,000-grain limit water softeners. At first, look no doubt the 24,000-grain framework would be perfect utilizing our illustration above, where we’re searching for 21,000 grains of aggregate softening limit. Tragically the affiliates of the 24,000-grain framework neglect to uncover that it takes 27 pounds of salt to completely recover this framework to the 24,000-grain level. A more precise portrayal of the “24,000” framework is “0.75 cubic feet”. So, be careful before choosing the right size. It is not as simple as it looks.